Buy BIS IS (R) SPECIFICATION FOR DRY-TYPE POWER TRANSFORMERS from SAI Global. Since dry-type power transformers are not made for such high voltages and ratings as oil-immersed transformers, a large portion of IS: * serves no purpose. pdf – Download as PDF File .pdf), Text File .txt) or read online. SPECIFICATION FOR DRY-TYPE POWER TRANSFORMERS Transformers Chairman.
|Published (Last):||6 March 2011|
|PDF File Size:||17.92 Mb|
|ePub File Size:||4.48 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dry-Type Power Transformers advertisement. This test shall be repeated with another line terminal earthed.
Calibration is carried out as described in Appendix A of IS: Part 1 General Jirsi reuision. Part 2 Measuring voltage transformers jirst rruision.
The choice between Lists 1 and 2 should be made by considering the degree of exposure to lightning dgy switching overvoltages, the type of system neutral earthing and, where applicable, the type of overvoltage protective device. Part 1 General jrst revision.
Afo NOTE – necessary. In addition to high or low ambient temperature and high altitude, other environment conditions which may affect design and transformres can exist and are not necessarily covered by this standard.
IS (): Dry-Type Power Transformers
Part 4 Terminal markings, tappings and connections Jirst revision. Guidance may be obtained from When the test frequency duration of the test shall be: Documents Flashcards Grammar checker.
Oblique strokes shall be used to separate the group of symbols for different cooling methods for the same piece of equipment. If it is, the degree of protection of the enclosure see Part 2 Temperature-rise 14 Jirst rctisioh.
NOTE – In view of the fact that the transtormers will be operated at two different taps the winding temperature-rise transformerz two transformer may be slightly different. The procedure shall be as given in Part 4 Terminal markings, tappings and connections first rcvition 12 vectorrela- IS: While interpreting the results, appropriate corrections to the temperature-rise should be made in accordance with For greater altitudes, see 3.
Part 38 Transformers first revision. Part 4 Capacitor voltage transformers Jirst revision. The provisions out by mutual 18 ; of acoustic sound level 19 ; and test Furthermore, in the transdormers of a single-phase phase-to-neutral and tested according to Geafol encapsulated dry-type transformers are required for indoor installations where safety and.
IS 11171 (1985): Dry-Type Power Transformers
These ratings shall be such that the transformer can deliver its rated current under steady loading conditions without exceeding the limits of temperature-rise specified in Section 3, assuming that the applied voltage is equal to the rated iw and that the supply is at rated frequency. It may be performed on all kinds of dry-type transformers, but is especially applicable to transformers having encapsulated windings. IS1 marked products are also continuously checked by IS1 for transformerx to that standard as a further safeguard.
The repetition rate of calibration pulses should be of the order of twice the frequency of the excitation voltage. Temperature tests are made by utilizing the rises obtained tests, one with no-load loss only, and one with load losses only, short-circuit run. The principles of the standard IS: Details of conditions, under which a licence for the use of the IS1 Certification Mark may be granted to manufacturers or processors, may be obtained from the Tjpe Standards Institution.
All other transformers shall be identified by four symbols for each cooling method for which a rating is assigned transfoemers the manufacturer. Enclosed or non-enclosed non-encapsulated-winding dry-type transformers are normally designed for installation indoors in dry locations.
Cast Resin Type Transformer Manufacturer in India Industrial Electrical Corporation
Tdansformers 3 Insulation 21 levels transformer and for each of levels, lim;ts, and dielectric tests B Part 3 Protective current transformers jfirst revision.
For the purpose of determining when constant temperature conditions have been achieved, thermocouples, thermistors, RTDs or thermometers shall be applied to the following surfaces: NOTE – The cooling of a dry-type or forced circulation.
Part 3 Protective voltage transformers jirst revision. The low-voltage winding shall transformdrs supplied from a three-phase or single-phase source, depending on whether the transformer itself is three-phase or single-phase.